Many air conditioners have indicators that show the cause of the failure. This helps to cope with some common problems right at home. Malfunctions are divided into the most common ones, which can be fixed on your own, and those that require serious repair in the service center. Below are the most common problems.
Sharp AF-S60FX air conditioner troubleshooting
|No display on panel or any one of the buttons failure. Remote control failure.||Transformer (Discharge transformer before testing)||Check resistance between the two input/output lines on transformer. Replace the transformer if either of the input/output is open or the transformer is damaged.|
|Display board or main PCB failure||Check the voltage of display board. Replace the display board if it is +5V else replace the main PCB.|
|Battery failure||Check the voltage of battery. Replace batteries if the voltage is lower than 2.3V.|
|Stop instantly after startup.||Refrigerant||The amount of the refrigerant is too much, making the compressor load too big. Recy- cle and recharge the refrigerant after checking for the reason.|
|Compressor||The compressor is seized. Replace after checking for the reason.|
|Fan motor will not run.||Transformer (Discharge transformer before testing)||Check resistance between the two input/output lines on transformer. Replace the transformer if either of the input/output is open or the transformer is damaged.|
|No power||Check voltage at electrical outlet. Correct if none.|
|Power supply cord||Check voltage at the power cord terminal on Main PCB. Replace the power cord if none.|
|Wire disconnected or connection loose||Connect wire. Refer to wiring diagram for terminal identification. Repair or replace loose terminal.|
|Main PCB failure||Select fan speed and Check the voltage on main PCB. Replace the main PCB if no voltage in all three.|
|Capacitor (Discharge capacitor before testing)||Test capacitor. Replace if not within +/-10% of manufacture's rating. Replace if shorted, open or damaged.|
|Will not rotate||Fan blade hitting shroud or blower hitting scroll. Realign assembly. Check fan motor bearings. Replace the motor if motor shaft do not rotate.|
|Fan motor noise.||Fan||Replace the fan if cracked, out of balance, or partially missing.|
|Blower||Replace the blower if cracked, out of balance, or partially missing.|
|Loose screws||Tighten them.|
|Worn bearings||Replace the motor if knocking sounds continue when running or loose, or the motor hums or noise appears to be internal while running.|
|The compressor not to stop even the room temperature has got to the setting temperature.||Room temperature sensor||Check and replace if the temperature is open or damaged.|
|Main PCB||Check and replace the main PCB if the relay on PCB is shorted or damaged.|
|Compressor will not run while fan motor runs.||Voltage||Check voltage. Call Supply Authority if not within limits.|
|Wiring||Check the wire connections, if loose, repair or replace the terminal. If wires are off, refer to wiring diagram for identification, and replace. Check wire locations. If not per wiring diagram, correct.|
|Main PCB failure||Check voltage of main PCB. Replace the main PCB if open.|
|Capacitor (Discharge capacitor before testing)||Check the capacitor. Replace if not within +/-10% of manufacturers rating. Replace if shorted, open, or damaged.|
|Room temp sensor||Check the temperature setting if not at the coolest (in cooling mode) or the warmest (in heating mode). Set it if not.|
|Compressor||Check the compressor for open circuit or ground. If open or grounded, replace the compressor.|
|Insufficient cooling.||Air filter||Clean or replace if restricted.|
|Vent. Door||Close if open.|
|Unit undersized||Determine if the unit is properly sized for the area to be cooled or heated.|
|Condenser and Evaporator||Clean or replace if restricted.|
|Fan motor||Check the fan capacitor and replace if not within +/-10% of manufactures rating.|
|Room structure||Take proper measures to make the door and windows sealed well if gap is found.|
|Air flow||Clean or remove if any barrier is found to block the inlet/outlet wind flow of the unit.|
|Sunlight||Add a awning if the condenser is exposed to the sunlight.|
|Less refrigerant||Check the tubes for reasons of leakage. Recycle the refrigerant, correct the leakage points and recharge.|
|Capillary tube||Regulate the flow if capillary tube and make the evaporating temperature appropriate if the evaporator is frosted. Replace if blocked. Repair joint if leaking.|
|Compressor||The inlet and outlet valve of the compressor is damaged, making the low pressure connected with the high pressure. The refrigerating system can not produce high pres- sure and low pressure. Replace the compressor after checking for the reason.|
|Heat sources||Reduce if too many.|
|Excessive noise.||Copper tubing||Remove the cabinet and carefully rearrange tubing not to contact cabinet, compressor, shroud and barrier.|
|The unit starts and stops frequently.||Power supply||The input power supply voltage is too low. Call an electrician if not within limits.|
|Main PCB||Check and replace the main PCB if the relay on PCB is shorted or damaged.|
|Outdoor temperature||When the outdoor temperature is too high, the compressor will protect.|
|No cooling.||No power||Check the voltage. Call an electrician if no within the limit.|
|Wiring||Check the terminals. Repair and correct if loose.|
|Temperature setting||Check and adjust the temperature setting.|
|Mode setting||Check and adjust the mode setting.|
|Main PCB||Check the voltage of main PCB. Replace the main PCB when the unit failure in heating mode.|
Sharp CV-P12PX air conditioner troubleshooting
|AIR CONDITIONER DOES NOT OPERATE AT ALL||• Is the unit plugged in or is the plug loose?
• Has the fuse blown or is the circuit breaker tripped?
• Did you restart the unit within 3 minutes of a power failure? If the power was off for less than 3 minutes when, you restarted the air conditioner, a protective device may cause the compressor to shut off, preventing cooling for about 5 minutes.
• Are the OPERATION, TIMER and MEGA COOL lamps blinking? The water tank inside the unit is full. It must be drained.
• Check the power plug. AIR CONDITIONER DOES NOT COOL PROPERLY
• Is it set to FAN, DEHUMIDIFICATION or VENTILATION mode? Cooling does not take place in these modes. Change the MODE setting.
• Is the filter clogged with dust? Clean the filter.
• Is the cooling coil frozen? No air will blow out if the cooling coil is frozen. Run the air conditioner in FAN mode with the fan speed set to "HIGH" until all ice dissipates.
• Is the temperature set properly?
• Is the window exposed to direct sunlight? Close the curtains or blinds to minimize solar energy heating the room.
• Is the exhaust hose too long? For efficient operation, make the hose as short as possible. The exhaust hose must not be twisted or bent.
|SOUNDS||• The unit may seem rather loud for the first 2 to 3 minutes when the unit is turned on. This is the sound of the compressor starting-up and is perfectly normal.
• A soft, swishing noise can be heard immediately after the unit is turned on or off, and also during operation. This is the sound of the refrigerant flowing inside the unit.
• A low buzzing noise is emitted when the unit is generating Plasmacluster ions.
• This air conditioner evaporates water condensed during cooling operation within the unit through the exhaust air outlet. Although water flowing sound way be heard, this is normal.
• An audible gurgling sound may be heard when the unit is operated on a gently sloping floor. Place the unit on a level floor.
|TIMER DOES NOT WORK PROPERLY||• If a power failure occurs while the TIMER is set, the TIMER setting will be cancelled and will not be retrieved even after the power is restored. This is normal for this unit.|
|THE UNIT FAILS TO REACT TO THE REMOTE CONTROL SIGNAL||• Check the batteries in the remote control. Replace if necessary.
• Try to send the signal again with the remote control pointed directly at the unit’s signal receiver window.
• Check whether the remote control batteries are installed with the polarities properly aligned.
|THE DISCHARGED AIR HAS AN ODOR||• Plasmacluster ion generator emit small traces of ozone which may produce an odor. These ozone emissions are below safety levels.|
Sharp GX-X18JR air conditioner troubleshooting
|The unit does not operate at all||Phase reverse or fuse broken||Change phase or replace fuse|
|Power off||It will restart when power is on|
|Loose plug||Put the plug into place|
|Batteries of remote controller fall||Replace batteries|
|Out of the remote controlling range||Keep distance in 10 m or less|
|Operation stops suddenly||There is obstacle at the air intake or outlet.||Remove it|
|The unit fails to cool (or heat) the room effectively||There is obstacle at the air intake or outlet.||Remove it|
|Wrong temperature setting||Refer to p.5|
|Low fan speed||Refer to p.5|
|Air direction is not correct||Refer to p.6|
|The door or window is open.||Close them|
|Direct sunshine||Close the curtain or blinder|
|There is heat source or too many people in the room.|
|The air filter is dirty or blocked.||Clean it|
|The unit does not operate||when you restart the unit||This is to protect the internal mechanisms. Wait 3 minutes before operating the unit.|
|when power is switched on||Wait for 1 minute|
|Mists come out||when cooling||Room air is chilled rapidly and becomes foggy|
|Outdoor unit is hot||after the unit is stopped||Compressor is emitting heat to get ready for restarting|
|Noise||Buzz is heard at starting||It's the starting sound of thermostat and will turn low after 1 minute|
|Sound of running water can be heard during operation||This is caused by the refrigerant flowing inside the unit|
|As huhsound is heard when unit starts/stops operation or defrost.||This is the noise of refrigerant caused by flow stop and flow change|
|A continuous low "shah" sound is heard during cooling operation or at a stop.||The noise is heard when the drainage pump is in operation|
|Cracking noise can be heard during or after operation||This sound is generated by the friction of the front panel and other components expanding or connecting due to a temperature change|
|Dust from the unit||Starting operation after not using for a long time.||Dust absorbed by the unit blows out|
|Odors||During operation||Carpet and furniture odors that entered into the unit may be sent out from the unit|
Sharp KC-6400E air conditioner troubleshooting
|SYMPTOM||REMEDY (not a malfunction)|
|Odours and smoke are not removed.||• Clean or replace the filters if they appear to be heavily soiled. (Refer to E-15.E-18)|
|The CLEAN-SIGN Light illuminates green even when the air is impure.||• The air could be impure at the time the unit was plugged in. (Refer to E-6) Pull out the plug from the electrical outlet, and insert the plug one minute later.|
|The CLEAN-SIGN Light illuminates orange or red even when the air is clean.||• The sensitivity of the sensors become unstable when the opening of the odour sensor or dust sensor is dirty or is clogged. Clean the dust around the sensor opening using a vacuum cleaner. (Refer to E-14)|
|A clicking or ticking sound is heard from the unit.||• Clicking sound or ticking sound is emitted when the unit is generating ions.|
|The discharged air has an aroma or odour.||• Check to see if the filters are heavily soiled. Replace the filters.|
|• Plasmacluster Air Purifiers emit small traces of ozone which may produce an odour. These ozone emissions are well below safety levels.|
|The unit does not operate when cigarette smoke is in the air.||• Is the unit installed in a location that is difficult for the sensor to detect cigarette smoke?|
|• Are the dust or odour sensor openings blocked or clogged? (In this case, clean the openings.) (Refer to E-14) (Care Cycle : MIST Filter: 1 month)|
|The MIST Filter Indicator Light remains activated even after replacing filter.||• After replacing filters, connect the power cord to an outlet and press the Mist Filter Reset Button. (Refer to E-17)|
|The Plasmacluster Indicator Light or the CLEAN-SIGN Light will not activate.||• Check to see if the Lights OFF Mode selected. If so, then press the Plasmacluster ON/OFF Button for 3 seconds to activate the indicator lights. (Refer to E-13)|
|Plasmacluster Indicator Light repeat colour cycles between light and shade.||• The ION SHOWER operation is working.|
|The Mist Filter Indicator Light does not turn on even water is in.||• Please check if the impurities adhered to the surface of the Float. Clean the Mist Tray. Check to see if the Main Unit is put on a inclined surface.|
|When the water of the tank does not decrease or the decrease of the water is slow.||• Check to see if the Mist Tray and Tank are installed correctly.|
|• Check the Mist Filter. Replace the filter when it is heavily soiled. (Refer to E-17,18)|
|The CLEAN-SIGN LIGHT switches frequently.||• The CLEAN-SIGN Light will automatically switches the colours when detected by dust and odour sensors.|